|Sand Filter Inlet- Outlet Water Filtration
|Treated Waste Water
|22 January 2024
The Filternox Engineering and Testing Team was present at the Iron-Steel Factory facility from January 22nd for a duration of 1 day to conduct filtration tests. The inlet water of the sand filter was tested with the Filternox® FMS-V-MR Model filter with a 40-micron rating, and the outlet water was tested with the Filternox® FMS-V-MR Model NTU Terminator filter. The data obtained from the measurements has been documented and reported.
1- System Definition
Picture 1.1. Filtration System Image
2- Filtration Test Measurement Results
2.1- Sand Filter Inlet Water – 40 micron Filternox® FMS-V-MR Model Filter
Picture 2.1. Filternox® 40 Micron FMS-V-MR Model Filter Sample Measurement Results
2.2- Sand Filter Outlet Water-Activated Carbon Inlet Water – Filternox® NTU Terminator FMS-V-MR Model Filter
Picture 2.2. Filternox® NTU Terminator FMS-V-MR Model Filter Sample Measurement Results
If the water sample’s TSS value is under 0 ppm , an underrange result is obtained.